The point of intelligent manual call is loop powered and operates on 17-35V dc.
The address of each call point is set in the commissioning stage by means of a DIL switch.
A solid red alarm LED is provided in the manual call point. This LED is controlled irrespective of the point of call, Control panel. The LED will flash yellow if there is a fault and flashes green when the device is searched. Discovery and configurable CoreProtocol.
Once activated, intelligent manual call point can be reset by inserting the reset button on the LED facing forward, turning clockwise until a positive click and redefinition occur.
The intelligent manual call point incorporates a short circuit isolator to ensure its operation in case of a short circuit in the circuit. The isolator operation is indicated by a solid yellow LED. For more details on the insulator, see data sheet PP2090, available upon request.
This manual call point helps reduce installation time, For all the initial installation cable is connected to a removable terminal block that fits perfectly on the back of the manual call point.
The call point components are molded in a fire resistant polycarbonate.
Compatible with XP95, Discovery e CoreProtocol
The smart manual call point will work with compatible Apollo control equipment using the XP95 protocols, Discovery and digital CoreProtocols.
EMC Directive 2014/30 / EU
The point of intelligent service manual complies with the essential requirements of the EMC Directive 2014/30 / EU, provided it is used as described.
A copy of the Declaration of Conformity is available from Apollo, upon request.
Compliance intelligent manual call point with the EMC Directive does not confer compliance with the policy on any device or system connected to it.
Regulation of construction products 305/2011
The point of intelligent service manual complies with the essential requirements of Regulation of construction products 305/2011.
A Performance Statement copy is available at the Apollo, upon request.
The manual call point Smart is designed to operate in a loop of intelligent fire detection devices. An alarm is initiated by pressing the resettable element. The manual call point signals to the machine control and indication using an interrupt feature in Apollo digital protocol. An alarm status is indicated by the rotation of the reconfigurable element, displaying yellow and black indication bars and a solid red LED. The manual call point can be easily reset by using the provided front reset button.
- resettable operating element
- Easy access, Front reset mechanism
- System for fitting and installation Z
- ergonomic reset button
- Certified in 54-11 the AND 54-17
- visible LED 170 °
- continuity link for cable insulation tests
- Suitable for semi-embedded or surface mount